View and Download Regin CORRIGO L10 manual online. CORRIGO L10 Controller pdf manual download. Click to download: >>> Download regin corrigo l10 manual >> Download songs computer memory card corrigo l10 manual. Corrigo design ergonomic chair, back pain, posture correction, office chair. EUR ; 0 bids; + EUR postage. 4d 11h left (Tuesday, ).
|Published (Last):||2 April 2005|
|PDF File Size:||16.33 Mb|
|ePub File Size:||5.22 Mb|
|Price:||Free* [*Free Regsitration Required]|
Controllers – Regin
Don’t show me this message again. This means that non-technical staff can feel secure while. Outputs Shows present values for AO Configuration Controlling plate heat exchanger Plate heat exchanger means that the output controls e.
Outputs can be set manually.
Settings Menu cofrigo If the user attempts to make changes that cannot be made or which lie outside his user level the codrigo will display the following information: The setpoint is compensated with respect to the temperature at outdoor temperature sensor AI1. Commissioning protocol Site System Date Commissioned by: AO3 make up the temperature controlling sequence.
The sequence or- der, however, is always the same: The controller has a display and built in indicator on the front for alarm and is operated by means of clearly defined buttons.
Operating buttons Up corriho – scrolls upwards in menu selections. Scheduler L10 has a scheduler based on a one-week period. Pg 1 No value written means default value Configuration Default setting Actual setting Config code This code number is time limited.
By pressing ‘print’ button you will print only current page. Outdoor compensation, breakpoint 1. Outdoor temperature or external setpoint Room temperature Supply air temperature Frost protection sensor When frostprotection is selected with water heater or Overheat protection When electric heater is used L0 Fan malfunction or fan status indicator.
Comments to this Manuals Your Name. The required functions are selected with the help of questions in normal script or by. L10 is a new controller which has been designed to be easy to use and.
During normal operation, without pressing any buttons, the display also shows the. The controller has been designed for mounting on a DIN rail, in norm housing or on. Page 22 Scheduler L10 has a scheduler based on a one-week period.
Y1 on increasing heat demand. Controllers for heating, boiler and ventilation applications in buildings.
Enter text from picture: The scheduler can handle power losses for corrig least 24 hours without cprrigo of data. Menu information If the user attempts to make changes that cannot be made or which lie outside his user level the controller will display the following information: If no status running signal is present at DI1 after a preset delay time, a fan alarm is activated and the system stops.
It has been designed for use in less complex air-handling systems.
REGIN CORRIGO LLON  $ –
Table Of Contents Automatic restart after changing When one or more parameters have been changed the controller will restart when the user leaves the configuration menu. On ice build-up the defrosting function xorrigo activated. Unauthorized No changes in Make new logon this menu Alarms When alarms are activated they are displayed in the alarm queue and also as a flashing red light on the display panel on the front of forrigo controller in the event of an alarm.
Y1 Automatic Reset Configuration Controlling plate heat exchanger Plate heat exchanger means that the output controls e. Outdoor compensation Values for compensation can be freely set but the breakpoints should be ordered with the highest highest outdoor temp at 4 and lowest lowest outdoor temp at 1.
Temperature At increasing heat requirement Y3 is always activated first, then Y2 and finally Y1. This requires user level 1. To print the manual completely, please, download it. Page of 30 Go. Configuration Supply air control with outdoor temperature compensation Coorrigo air control with outdoor temperature The temperature sensor Supply Air AI3 controls the sequences to corriyo setpoint.
If you enter the?
The menu system works with different user-levels to show settings and to allow. If the key is held in depressed position it will repeat.
The AI4 input is used as a digital input cofrigo the unit is configured with overheat protection on an electric heater. Explanation of control Which parameters are shown or hidden depends on which control function has been funktions selected.
DI1 has to be closed. Page 8 Operating buttons Up arrow – scrolls upwards in menu selections.